The first thing you need to do is run a simple test on your well pump to get an approximate gallon per minute figure. This is important due to the fact that iron filters and Ph filters need 5 gallons per minute minimum to backwash properly.
This is how you do the test:
How to size the system is limited to what size you can backwash properly. If your pump is capable of backwashing the largest of these systems, then do the following to size the system.
A home with the following will require the following size iron filter or ph filter:
Up to two bathrooms with a home up to 3,000 sq.ft. a 1.0 cubic foot iron or ph filter system is required.
Up to three bathrooms with a home up to 4,000 sq.ft. a 1.5 cubic foot iron or ph filter is required.
Up to 5 bathrooms with a home up to 5,000 sq.ft. a 2.0 cubic foot iron or ph filter is required.
Up to 6 bathrooms with a home up to 6000 sq.ft. a 2.5 cubic foot iron or ph filter is required.
1 ) Amount of full bathrooms in home.
2 ) Any multi body sprayers in one shower stall
3 ) Square footage of home.
Note: If you do not have a well pump that produces enough gallons per minutes needed for a larger system, but have a lot of bathrooms that will be used at the same time, then you have a few choices. Install a larger pump or purchase a system that you can backwash and minimize the amount of fixtures being used at the same time.
If your iron content is less than 7 Mg/L or ppm with no hydrogen sulfite ( Sulfur ) and the iron is in a physical form with a ph balance between 6.8 to 9.0 then a Birm filter is a good choice.
Terminator System: If the iron is between 7 and 11 Mg/L or ppm then you will need to either purchase the terminator system, which is a Birm filter with an air injector and air precipitation tank to enhance the performance of the Birm filter. Or install a water softener with fine mesh resin to remove the rest of the iron from the water. A terminator system with a water softener using fine mesh resin will remove up to 20 Mg/L or ppm iron, sulfur up to 5 Mg/L or ppm, and up to 3 Mg/L or ppm manganese from the water.
If your iron content is less than 7 Mg/L or ppm with hydrogen sulfite ( Sulfur ) and the iron is in a dissolved or physical form with a ph balance between 6.8 to 9.0 then a greensand filter or terminator is a good choice and will remove up to 11 Mg/L or ppm Iron, 5 Mg/L or ppm sulfur, and 3 Mg/L or ppm manganese from the water.
If your Iron content is 20 Mg/L or ppm or above; we recommend that you install a greensand filter, and use a stenner chemical feed pump. Using a feed pump with a 120 gallon retention tank for contact time so the chlorine or 7% hydrogen peroxide can oxidize the iron, manganese and sulfur will allow the greensand filter to remove it more readily. A 1.5 cubic foot centaur backwashing carbon filter to filter out anything that the greensand filtered missed, and to either remove the chlorine residue from the water or convert any residual of peroxide back in to oxygen should follow. Add on a 2510SXT – 80,000 grain capacity water softener using fine mesh resin.
Raising the pH of your water to 7.0 is done by using a pH neutralizer. A pH neutralizer uses a media called calcite limestone in it (crushed milled marble manufactured for the purpose of water treatment). Choose the size of the Ph Neutralizer as shown on slide 3.
We hope this information has helped you in your quest for choosing the correct Iron Filter for your needs!
For additional help and/or information please contact us at 866-278-4130 or fill out our contact form.
Water Treatment Industry Links Water Treatment Equipment, Water Softener Reviews, Water Softeners, Water Filter Systems, Best Quality, Best Price Water Softeners, Low Price, Full Service Water Filtration Company, Water Softners, Water Softening, Water Softner, Internet Wholesale Distributor Of Quality Residential and Commercial Water Treatment Equipment Parts and Supplies, Reverse Osmosis Filters, Ultraviolet Sterilizers, Iron Filters, Water Softener, Water Softeners, Magnetic Water Softeners, Saltless Water Softeners, Water Softener Reviews, Magnetic Water Softener, Home Water Softeners, Water Softener Systems, Home Water Softener, Water Softener Comparison & Ratings, Commercial Water Softener, Water Softener Installation, How To Install A Water Softener, How Does a Water Softener Work, Sizing a Water Softener, Differences Between Big Chain Store Bought Systems And A Professional Water Treatment Dealer, Reverse Osmosis Water Filter, Reverse Osmosis Filter System, Reverse Osmosis Filters, Reverse Osmosis Water Filters, Reverse Osmosis Filter, Reverse Osmosis Water Filter Systems, Ultraviolet Water Filter, Iron Water Filter, Water Conditioners, Water Purifiers, Ozone Systems, Manganese Filters, Triple O Systems, Ph Neutralizers, Acid Filters, Ph Filters, Fleck Water Softeners, Autotrol Water Softener, Ge Water Softeners, General Electric Water Softeners
New York, San Diego, Dallas, San Antonio, Orlando, Los Angeles, Chicago, Houston, Philadelphia, Phoenix, Detroit, San Jose, Indianapolis, San Francisco, Washington DC, Nashville Davidson, El Paso, Seattle, Denver, Charlotte, Fort Worth, Yonkers, Spokane, Glendale, Calgary, Edmonton, Halifax , Montreal, Ottawa, Toronto, Vancouver, Victoria, Winnipeg, London, Hamilton, and Quebec, Portland, Oklahoma City, Tucson, New Orleans, Las Vegas, Cleveland, Long Beach, Albuquerque, Kansas City, Fresno, Virginia Beach, Atlanta, Sacramento, Oakland, Mesa, Stockton, Birmingham, Jersey City, Norfolk, Baton Rouge, Hialeah, Lincoln, Jacksonville, Columbus, Austin, Baltimore, Memphis, Milwaukee, Boston, Greensboro, Plano, Rochester, Glendale, Akron, Garland, Madison, Fort Wayne, Bayamon, Puerto Rico, Fremont, Scottsdale, Montgomery, Shreveport, Augusta, Lubbock, Chesapeake, Mobile, Des Moines, Grand Rapids, Tulsa, Omaha, Minneapolis, Honolulu, Miami, Colorado Springs, St. Louis, Wichita, Santa Ana, Pittsburgh, Arlington, Cincinnati, Anaheim, Toledo, Tampa, Buffalo, Saint Paul, Corpus Christi, Aurora, Raleigh, Newark, Lexington, Anchorage, Louisville, Riverside, Saint Petersburg, Bakersfield, Richmond
Canada, Water Softerners for Alabama, Alaska, Arizona, Arkansas, California, Colorado, Connecticut, Delaware, Florida, Georgia, Hawaii, Idaho, Illinois, Indiana, Iowa, Kansas, Kentucky, Louisiana, Maine, Maryland, Massachusetts, Michigan, Minnesota, Mississippi, Missouri, Montana, Nebraska, Nevada New Hampshire, New Jersey, New Mexico New York, North Carolina, North Dakota, Ohio, Oklahoma, Oregon, Pennsylvania, Rhode Island, South Carolina, South Dakota, Tennessee, Texas, Utah, Vermont, Virginia, Washington, West Virginia, Wisconsin, Wyoming